Retrofit incorporating Howden VN sealing system brings long-term leakage control and significantly reduces the unit heat rate and operating costs.
The introduction of Howden's VN seal system to the air preheaters brought an immediate drop in leakage level from 26% to 5%. Over the subsequent eight years, the level has been maintained at an average of 5.75%.
Almeria Thermal Power Plant, Spain uses two 550 MW coal fired generating units. When the newer of the two was installed the air preheaters were fitted with Howden VN seals that gave reliable leakage control with minimal maintenance.
An opportunity to upgrade the older unit arose when leakage drift rose to crisis levels. The size 32 air preheaters in the unit were equipped with actuated sector plates that relied on sensors and articulated elements – a system that worked well initially but is unsuitable for the corrosive and erosive conditions in which it was installed. In a relatively short time, it stopped working and the leakage rose to very high levels – too high for proper operation of the generating unit. As a consequence, the power consumption of both the FD and ID fans also rose to unacceptable levels and the associated increase in the unit heat rate was further exacerbated by the effects of hot end leakage. The excessive leakage and the associated overburdening of the ID fan can also play a part in reducing the unit's output.
Howden recommended and installed a VN sealing system similar to the one that was giving good service in the newer Almeria generating unit. The VN system uses fixed sector plates and double sealing and has proven its value in over 1000 installations worldwide.
The fixed plates require no actuation mechanism and the increased hot end seal gaps are compensated for by an increased number of radial walls so that there are two radial seals forming a labyrinth under the sector plate at all times.
The introduction of the VN system into the Almeria Power Station has considerably reduced leakage, increased availability and reduced maintenance costs. The radial seals gave problem-free service for five years before any replacement was required.
The double sealing principle
In an air preheater, radial leakage typically accounts for around 70% of the total leakage. The Howden VN double seal system, which has been operating successfully for more than 30 years in both new installations and retrofit projects, substantially reduces these losses. Double sealing can usually be achieved by increasing the number of radial walls or by widening the sector plate. The result in both cases is that there are two or more radial seals under the sector plate at all times and the seal leakage is reduced by a factor of 1/√2.
The advantages of a fixed sector plate
Sealing systems that depend on articulated parts that are moved by actuators and controlled by sensors are extremely vulnerable in hazardous environments.
Factors such as erosion from ash and corrosive atmospheres greatly impair their durability, and significant maintenance is required to keep them working at acceptable levels of availability.
By eliminating the need for moving parts, the fixed sector plate offers a far more reliable long-term control of leakage. Thermal capping of the rotor is accommodated by the parabolic design of the bottom sector plate, which offers maximum adaptability to the radial seals.
Full List of Case Study pages
The introduction of Howden's VN seal system to the air preheaters brought an immediate drop in leakage level from 26% to 5%.
Howden completed a retrofit of VARIAX ID fans on the 640MW unit 5 at Asnaes Power Station, Denmark.
The Howden Free Floating Piston is a proven unique technolgy that turns the weakest point to one of the strongest, which removes rider bands wear at a stroke
Berre Petrochemical Cluster, which includes polypropylene and polyethylene plants, trusted Howden to reduce its power costs by 7% within a 3 year return on investment.
VentSim CONTROL technologies result in impressive cost and energy savings while also raising productivity at Goldcorp Eleonore gold mine.
Fresnillo mine is one of the most technologically advanced deep mines in the world, and incorporates VentSim CONTROL ventilation management.
UPTIME provides advanced compressor performance analysis at Gunvor Petroleum in the Netherlands
Howden worked with a North American hard rock mine to introduce a Ventilation on Demand system using VentSim CONTROL technology.
Installing a bigger hub at Herningvaerket, reducing installation costs and future service expenses.
The understanding and knowledge provided by Howden is an essential factor when installing additional equipment on your compressors.
New integrally geared compressor (IGC) results in power savings up to 31MW/h a day
Replacement of primary plate heaters with Howden custom designed rotary air preheaters.
200 bar to 300 bar hybrid compressor retrofit for helium capacity filling
At Millmerran Power Station, Howden provides a tailored service that supports their needs of the plant to prepare for their upcoming major outage.
New boiler and FGD processes called for a total change of the ID booster fan at a power plant in Plzen
Howden develop method to drastically reduce the cylinder repair time of reciprocating compressors.
Upgrade your reciprocating compressor with our innovative coated liner solution.
The introduction of Howden's HC element to the air preheater resulted in extended operational times.
Huge savings were realised by using Howden's turnkey service to reduce heater leakage and running costs.
A large chemical plant on the east coast of the United States contacted Howden to perform a full Turnkey project on their critical path air preheaters.
Howden expertise solves long lasting problems with an axial fan at Uniper's Franken plant.
During the first few months after the deployment of Uptime, VEAS experienced two distinct challenges where the benefits of Uptime were clearly demonstrated.
VentSim CONTROL case study for three typical mining projects.
Replacement of existing blades at the Wangqu Thermal Power Station
Efficient engineering solves impeller failures at the Wibank coalfield.
At Tarmac (Dunbar cement plant, UK), their existing Raw Mill fan was replaced with an enhanced Howden design in 2007.
Building the world's biggest reciprocating compressor - a white paper and video.
If you would like to submit an enquiry please get in touch.