DONG Energy, the largest Danish utility company, generates electricity for distribution throughout Northern Europe. Howden completed a retrofit of VARIAX® ID fans on the 640MW unit 5 at Asnæs Power Station, Denmark in 2003.
To meet the additional system resistance that occurs when adding an SCR system, the fan performance of the existing ID fans had to be increased by approx. 1500Pa.
To date the upgraded fans and their performance have exceeded the client's expectations. The combination of Howden technology know-how and smooth project execution ensured that the overall outage period for the client was reduced to a minimum.
To protect the environment and comply with European environmental legislation, the client had to reduce the emission of oxides of nitrogen (NOx) by installing a selective catalytic reduction (SCR) system. To meet the additional system resistance that occurs when adding an SCR system, the fan performance of the existing ID (induced draught) fans had to be increased by approx. 1500Pa.
The existing VARIAX ID fans were supplied back in 1978; the actual supply consisted of two single-stage fans, ASN-3400/2000S, 990rpm, 6628Pa, each with a 4200 kW motor. The original hubs were made of spherical cast iron and equipped with forged aluminium blades with erosion shields.
As the upgrade did not require any changes to the existing ductwork and foundations the final overall expense was considerably lower than that for installing new fans. The solution also provided the client with more efficient fans and an extension of the recommended service intervals.
Because the existing ID fans were incapable of meeting the increased pressure a solution with new fans or an upgrade of the existing fans had to be found.
Based on the latest technology developed, designed and tested in Howden's centre of excellence for axial flow fans in Naestved, Denmark, an upgrade solution was provided which did not require any changes to the existing ductwork connected to the fans or the existing foundations.
The main feature of the upgrade was the installation of our specially designed high pressure profile blades. The new blades were made of nodular cast iron that increases blade life considerably compared to the original aluminium. These new blades were fitted to a brand new bolted steel hub, which together with our unique oil-lubricated blade bearings extend service intervals significantly. As well as replacing the existing rotor components, new guide vanes in the inlet box and diffuser were installed and minor changes to the stator implemented.
A new main motor (customer supply) was also installed.
Full List of Case Study pages
The introduction of Howden's VN seal system to the air preheaters brought an immediate drop in leakage level from 26% to 5%.
Howden completed a retrofit of VARIAX ID fans on the 640MW unit 5 at Asnaes Power Station, Denmark.
The Howden Free Floating Piston is a proven unique technolgy that turns the weakest point to one of the strongest, which removes rider bands wear at a stroke
Berre Petrochemical Cluster, which includes polypropylene and polyethylene plants, trusted Howden to reduce its power costs by 7% within a 3 year return on investment.
VentSim CONTROL technologies result in impressive cost and energy savings while also raising productivity at Goldcorp Eleonore gold mine.
Fresnillo mine is one of the most technologically advanced deep mines in the world, and incorporates VentSim CONTROL ventilation management.
UPTIME provides advanced compressor performance analysis at Gunvor Petroleum in the Netherlands
Howden worked with a North American hard rock mine to introduce a Ventilation on Demand system using VentSim CONTROL technology.
Installing a bigger hub at Herningvaerket, reducing installation costs and future service expenses.
The understanding and knowledge provided by Howden is an essential factor when installing additional equipment on your compressors.
New integrally geared compressor (IGC) results in power savings up to 31MW/h a day
Replacement of primary plate heaters with Howden custom designed rotary air preheaters.
200 bar to 300 bar hybrid compressor retrofit for helium capacity filling
At Millmerran Power Station, Howden provides a tailored service that supports their needs of the plant to prepare for their upcoming major outage.
New boiler and FGD processes called for a total change of the ID booster fan at a power plant in Plzen
Howden develop method to drastically reduce the cylinder repair time of reciprocating compressors.
Upgrade your reciprocating compressor with our innovative coated liner solution.
The introduction of Howden's HC element to the air preheater resulted in extended operational times.
Huge savings were realised by using Howden's turnkey service to reduce heater leakage and running costs.
A large chemical plant on the east coast of the United States contacted Howden to perform a full Turnkey project on their critical path air preheaters.
Howden expertise solves long lasting problems with an axial fan at Uniper's Franken plant.
During the first few months after the deployment of Uptime, VEAS experienced two distinct challenges where the benefits of Uptime were clearly demonstrated.
VentSim CONTROL case study for three typical mining projects.
Replacement of existing blades at the Wangqu Thermal Power Station
Efficient engineering solves impeller failures at the Wibank coalfield.
At Tarmac (Dunbar cement plant, UK), their existing Raw Mill fan was replaced with an enhanced Howden design in 2007.
Building the world's biggest reciprocating compressor - a white paper and video.
If you would like to submit an enquiry please get in touch.